Delivery pvc and hdpe pipe for the city of deland - sperling rwm.
Invitation to Bid: Furnish and deliver pvc and hdpe pipe for the city of deland - sperling rwm
Pipe shall be delivered the various jobsites in truckload quantities. Supplier shall stage delivery (and billing) over an estimated period of 60 to 120 days as required to meet the City s installation contractor s schedule. POLYVINYL CHLORIDE (PVC) PIPE AND FITTINGS A. Polyvinyl chloride pipe for 4 inches and larger in diameter for pressure service shall conform to the requirements of AWWA C900 with a dimension ration of DR 18, pressure class 150, and gasketed integral bell ends. Pipe shall be extruded purple in color for reclaimed water main pipe. Pipe shall be delivered in 20 lengths. HIGH DENSITY POLYETHYLENE PIPE (HDPE) A. HDPE Pipe, PE 3408, in 4-inch and larger diameter for pressure service shall conform to AWWA C906. The pipe shall be produced to the dimensions and tolerances specified in ASTM F 714. The pipe shall be homogenous throughout and free of visible cracks, holes, voids, foreign inclusions, fillers, or other deleterious defects and shall be identical in color, density, melt index, and other physical properties throughout. Pipe shall be accepted for potable water use by the Florida Department of Environmental Protection. B. Pipe shall have a pipe diameter based on ductile iron pipe size (DIPS), a dimension ratio (DR) of 11, and has a minimum hydrostatic design basis of 200 psi with a maximum operating temperature of 74A. The HDPE pipe shall be black with three equally spaced pairs of purple stripes extruded into the pipe OD. C: HDPE shall be delivered in 40 lengths.
Tender documents : T25569691.html
2014 Al Bawaba (Albawaba.com) Provided by SyndiGate Media Inc. ( Syndigate.info ).
|Printer friendly Cite/link Email Feedback|
|Date:||Jan 21, 2015|
|Previous Article:||Outdoor Electronic Message Board.|
|Next Article:||Provide Professional Engineering Consulting Services for the American Tobacco District Waterline Replacement Project.|