Model validation and testing: the methodological foundation of ASHRAE Standard 140.
Ideally, whole-building energy simulation programs model all aspects of a building that influence energy use and thermal and visual comfort for the occupants. An essential component of the development of such computer simulation models is a rigorous program of validation and testing. This paper describes a methodology to evaluate the accuracy of whole-building energy simulation programs. The methodology is also used to identify and diagnose differences in simulation predictions that may be caused by algorithmic differences, modeling limitations, coding errors, or input errors. The methodology has been adopted by ANSI/ASHRAE Standard 140, Method of Test for the Evaluation of Building Energy Analysis Computer Programs (ASHRAE ASHRAE American Society of Heating, Refrigerating & Air Conditioning Engineers 2001a, 2004). A summary of the method is included in the 2005 ASHRAE Handbook--Fundamentals (ASHRAE 2005). This paper describes the ASHRAE Standard 140 method of test and its methodological basis. Also discussed are possible future enhancements to ASHRAE Standard 140 and related research recommendations.
Ideally, whole-building energy simulation programs model all aspects of energy use and thermal and visual comfort in buildings. Such programs may contain tens of thousands to hundreds of thousands of lines of code The statements and instructions that a programmer writes when creating a program. One line of this "source code" may generate one machine instruction or several depending on the programming language. A line of code in assembly language is typically turned into one machine instruction. . An error in even one character of one line of code can lead to seriously flawed results. Therefore, an essential component of the development of such computer simulation models is a rigorous program of validation, testing, and diagnostics. The United States United States, officially United States of America, republic (2005 est. pop. 295,734,000), 3,539,227 sq mi (9,166,598 sq km), North America. The United States is the world's third largest country in population and the fourth largest country in area. Department of Energy's National Renewable Energy Laboratory The National Renewable Energy Laboratory (NREL), located in Golden, Colorado, as part of the U.S. Department of Energy, is the United States' primary laboratory for renewable energy and energy efficiency research and development. (NREL NREL National Renewable Energy Laboratory
NREL Natural Resource Ecology Laboratory (Colorado State University, Fort Collins, CO) ) has developed an overall methodology to evaluate the accuracy of whole-building energy simulation programs and to identify and diagnose differences in simulation predictions that may be caused by algorithmic differences, modeling limitations, coding errors, or input errors. This method has been adopted by ANSI/ASHRAE Standard 140, Method of Test for the Evaluation of Building Energy Analysis Computer Programs (ASHRAE 2001a, 2004). The method has recently been summarized for inclusion in the 2005 ASHRAE Handbook -- Fundamentals (ASHRAE 2005).
ANSI/ASHRAE STANDARD 140
ASHRAE Standard 140 (ASHRAE 2001a, 2004) was the first codified cod·i·fy
tr.v. cod·i·fied, cod·i·fy·ing, cod·i·fies
1. To reduce to a code: codify laws.
2. To arrange or systematize. method of test for building energy software in the world and has recently been referenced by ANSI/ASHRAE/IESNA Standard 90.1 (ASHRAE 2001b, 2006) for approval of software used to show performance path compliance. Standard 140 is structured to allow for the addition of all elements of a complete validation approach as they become available. This structure corresponds to the validation methodology introduced above with subdivisions creating a matrix of six areas for testing, including:
1. Comparative tests -- building envelope A building envelope is the separation between the interior and the exterior environments of a building. It serves as the outer shell to protect the indoor environment as well as to facilitate its climate control.
2. Comparative tests -- mechanical equipment and on-site energy generation equipment
3. Analytical verification -- building envelope
4. Analytical verification -- mechanical equipment and onsite energy generation equipment
5. Empirical validation An empirical validation of a hypothesis is required for it to gain acceptance in the scientific community. Normally this validation is achieved by the scientific method of hypothesis commitment, experimental design, peer review, adversarial review, reproduction of results, -- building envelope
6. Empirical validation -- mechanical equipment and on-site energy generation equipment
This is a highly abbreviated way of representing the overall parameter space In generative art people talk about parameter space as the set of possible parameters for a generative system.
In statistics one can study the distribution of a random variable. Several models exist, the most common one being the normal distribution (or Gaussian distribution). in which building energy simulation programs operate, and each cell in the matrix represents a very large region in the space. The current set of tests are classified under categories 1 and 4. These tests are based on procedures developed by the NREL and field-tested by the International Energy Agency (IEA IEA International Energy Agency
IEA International Environmental Agreements
IEA International Association for the Evaluation of Educational Achievement
IEA Institute of Economic Affairs
IEA Inferred from Electronic Annotation
IEA International Ergonomics Association ) over three IEA research tasks (Judkoff and Neymark 1995a; Neymark and Judkoff 2002). The category 1 procedures (ASHRAE 2001a) were refined and converted to standards language and format by the ASHRAE SPC 1. (business) SPC - Statistical Process Control. Something to do with quality management.
2. (body) SPC - Software Productivity Centre.
3. (company) SPC - Software Publishing Corporation.
4. 140 Standards Project Committee. The category 4 procedures were refined and converted to standards language and format by ASHRAE Standing Standard Project Committee (SSPC SSPC Society for Protective Coatings (formerly Steel Structures Painting Council)
SSPC Steel Structures Painting Council (now Society for Protective Coatings) ) 140 and are included along with the category 1 procedures in the most recent revision of Standard 140 (ASHRAE 2004). Continuing oversight of Standard 140 by SSPC 140 allows validation procedures used within Standard 140 to evolve as the state of the art of whole-building energy simulation evolves. Additional tests have been--or are being--developed under ASHRAE research projects (Spitler et al. 2001; Yuill and Haberl 2002) and under a joint IEA Solar Heating and Cooling Solar heating and cooling
The use of solar energy to produce heating or cooling for technological purposes. Beneficial uses include distillation of sea water to produce salt or potable water; heating of swimming pools; space heating; heating of water for Programme and Energy Conservation in Buildings and Community Systems Task 34/Annex 43 (Judkoff and Neymark 2004) that are intended to fill in other categories of the above validation matrix.
METHODOLOGICAL BASIS FOR ANSI/ASHRAE STANDARD 140
There are only a few ways to evaluate the accuracy of a whole-building energy simulation program (Judkoff et al. 1983b):
* Empirical Validation -- in which calculated results from a program, subroutine A group of instructions that perform a specific task. A large subroutine might be called a "module" or "procedure." Subroutine is somewhat of a dated term, but it is still quite valid. , algorithm, or software object are compared to monitored data from a real building, test cell, or laboratory experiment.
* Analytical Verification -- in which outputs from a program, subroutine, algorithm, or software object are compared to results from a known analytical solution or a generally accepted numerical method for isolated heat transfer under very simple, highly constrained con·strain
tr.v. con·strained, con·strain·ing, con·strains
1. To compel by physical, moral, or circumstantial force; oblige: felt constrained to object. See Synonyms at force.
2. boundary conditions boundary condition
The set of conditions specified for behavior of the solution to a set of differential equations at the boundary of its domain. .
* Comparative Testing -- in which a program is compared to itself or to other programs.
Table 1 compares these techniques (Judkoff 1988). In this table the term model is the representation of reality for a given physical behavior. For example, heat transfer may be simulated with one-, two-, or three-dimensional thermal conduction thermal conduction
Transfer of heat energy resulting from differences in temperature between adjacent bodies or adjacent parts of a body. In the absence of a heat pump, the energy will flow from a region of higher temperature to a region of lower temperature. models. The term solution process encompasses the mathematics and computer coding to solve a given model. The solution process for a model can be perfect while the model remains inappropriate for a given physical situation, such as using a one-dimensional conduction conduction, transfer of heat or electricity through a substance, resulting from a difference in temperature between different parts of the substance, in the case of heat, or from a difference in electric potential, in the case of electricity. model where two-dimensional conduction dominates. The term truth standard represents the standard of accuracy for predicting real behavior. An analytical solution is a mathematical truth standard but only tests the solution process for a model, not the appropriateness of the model. An approximate truth standard from an experiment tests both the solution process and appropriateness of the model within experimental uncertainty. The ultimate (or "absolute") validation truth standard would be comparison of simulation results with a perfectly performed empirical experiment, with all simulation inputs perfectly defined.
Establishing an absolute truth standard for evaluating a program's ability to analyze physical behavior requires empirical validation, but this is only possible within the range of measurement uncertainty, including that related to instruments, spatial and temporal discretization dis·cret·i·za·tion
The act of making mathematically discrete. , and the overall experimental design. Test cells and buildings are large, relatively complex experimental objects. The exact design details, material properties, and construction in the field cannot be perfectly known, so there is some uncertainty about the simulation model inputs that accurately represent the experimental object. Meticulous care is required to describe the experimental apparatus as clearly as possible to modelers to minimize this uncertainty. This includes experimental determination of as many material properties and other simulation model inputs as possible, including overall building parameters such as overall steady-state heat transmission coefficient Transmission coefficient could refer to:
1. the pathological diffusion or accumulation in a tissue or cells of substances not normal to it or in amounts in excess of the normal.
2. infiltrate (2). rate, and thermal capacitance capacitance, in electricity, capability of a body, system, circuit, or device for storing electric charge. Capacitance is expressed as the ratio of stored charge in coulombs to the impressed potential difference in volts. . Also required are detailed meteorological me·te·or·ol·o·gy
The science that deals with the phenomena of the atmosphere, especially weather and weather conditions.
[French météorologie, from Greek measurements. For example, many experiments measure global horizontal solar radiation solar radiation,
n the emission and diffusion of actinic rays from the sun. Overexposure may result in sunburn, keratosis, skin cancer, or lesions associated with photosensitivity. , but very few experiments measure the splits between direct, diffuse, and ground-reflected radiation, all of which are inputs to many whole-building energy simulation programs.
The NREL methodology divides empirical validation into different levels because many past validation studies produced inconclusive INCONCLUSIVE. What does not put an end to a thing. Inconclusive presumptions are those which may be overcome by opposing proof; for example, the law presumes that he who possesses personal property is the owner of it, but evidence is allowed to contradict this presumption, and show who is results. The levels of validation depend on the degree of control over possible sources of error in a simulation. These error sources consist of seven types, divided into two groups.
External Error Types
* Differences between the actual microclimate microclimate
Climatic condition in a relatively small area, within a few feet above and below the Earth's surface and within canopies of vegetation. Microclimates are affected by such factors as temperature, humidity, wind and turbulence, dew, frost, heat balance, that affects the building versus weather input used by the program
* Differences between actual schedules, control strategies, effects of occupant occupant n. 1) someone living in a residence or using premises, as a tenant or owner. 2) a person who takes possession of real property or a thing which has no known owner, intending to gain ownership. (See: occupancy) behavior, and other effects from the real building versus those assumed by the program user
* User error in deriving building input files
* Differences between the actual physical properties of the building (including HVAC (Heating Ventilation Air Conditioning) In the home or small office with a handful of computers, HVAC is more for human comfort than the machines. In large datacenters, a humidity-free room with a steady, cool temperature is essential for the trouble-free systems) versus those input by the user
Internal Error Types
* Differences between the actual thermal transfer See thermal wax transfer printer and direct thermal printer. mechanisms in the real building and its HVAC systems versus the simplified model of those processes in the simulation (all models, no matter how detailed, are simplifications of reality)
* Errors or inaccuracies in the mathematical solution of the models
* Coding errors
The simplest level of empirical validation compares a building's actual long-term energy use to that calculated by a computer program, with no attempt to eliminate sources of discrepancy. Because this is similar to how a simulation tool is used in practice, it is favored by many in the building industry. However, it is difficult to interpret the results because all possible error sources are acting simultaneously. Even if there is good agreement between measured and calculated performance, possible offsetting errors prevent a definitive conclusion about the model's accuracy. More informative levels of validation involve controlling or eliminating various combinations of error types and increasing the density of output-to-data comparisons (e.g., comparing temperature and energy results at various time scales, ranging from subhourly to annual). At the most detailed level, all known sources of error are controlled to identify and quantify unknown error sources and to reveal causal relationships associated with the error sources.
This principle also applies to intermodel comparative testing and analytical verification. The more realistic the test case, the more difficult it is to establish causality causality, in philosophy, the relationship between cause and effect. A distinction is often made between a cause that produces something new (e.g., a moth from a caterpillar) and one that produces a change in an existing substance (e.g. and diagnose problems; the simpler and more controlled the test case, the easier it is to pinpoint sources of error or inaccuracy in·ac·cu·ra·cy
n. pl. in·ac·cu·ra·cies
1. The quality or condition of being inaccurate.
2. An instance of being inaccurate; an error. . Methodically me·thod·i·cal also me·thod·ic
1. Arranged or proceeding in regular, systematic order.
2. Characterized by ordered and systematic habits or behavior. See Synonyms at orderly. building up to realistic cases is useful for testing interactions between algorithms modeling linked mechanisms.
A comparison between measured and calculated performance represents a small region in an immense N-dimensional parameter space. Investigators are constrained to exploring relatively few regions in this space yet would like to be assured that the results are not coincidental co·in·ci·den·tal
1. Occurring as or resulting from coincidence.
2. Happening or existing at the same time.
co·in (e.g., not a result of offsetting errors) and do represent the validity of the simulation elsewhere in the parameter space. Analytical and comparative techniques minimize the uncertainty of the extrapolations around the limited number of sampled empirical domains. Table 2 classifies these extrapolations. Use of the term vice versa VICE VERSA. On the contrary; on opposite sides. in Table 2 is intended to mean that the extrapolation (mathematics, algorithm) extrapolation - A mathematical procedure which estimates values of a function for certain desired inputs given values for known inputs.
If the desired input is outside the range of the known values this is called extrapolation, if it is inside then can go both ways (e.g., from short-term to long-term data, and from long-term to short-term data). This does not mean that such extrapolations are correct, but only that researchers and practitioners have either explicitly or implicitly made such inferences in the past.
Figure 1 shows one process to combine the analytical, empirical, and comparative techniques. These three techniques may also be used together in other ways; for example, intermodel comparisons may be done before an empirical validation exercise to better define the experiment and to help estimate experimental uncertainty by propagating all known error sources through one or more whole-building energy simulation programs (Hunn et al. 1982; Lomas et al. 1994).
For the path shown in Figure 1, the first step is running the code against analytical verification test cases to check its mathematical solution. Discrepancies must be corrected before proceeding further.
Second, the code is run against high-quality empirical validation data and errors are corrected. Diagnosing error sources can be quite difficult and is an area of research in itself. Comparative techniques can be used to create diagnostic procedures (Achermann and Zweifel 2003; Judkoff 1988; Judkoff and Neymark 1995a, 1995b; Judkoff et al. 1983a; Judkoff et al. 1980; Morck 1986; Neymark and Judkoff 2002, 2004; Purdy and Beausoleil-Morrison 2003; Spitler et al. 2001; Yuill and Haberl 2002) and to better define empirical experiments.
The third step is to check agreement of several different programs with different thermal solution and modeling approaches (that have passed through steps 1 and 2) in a variety of representative cases. This uses the comparative technique as an extrapolation tool. Deviations in the program predictions indicate areas for further investigation.
When programs successfully complete these three stages, they are considered validated for cases where acceptable agreement was achieved (i.e., for the range of building, climate, and mechanical system types represented by the test cases). Once several detailed simulation programs have satisfactorily completed the procedure, other programs and simplified design tools can be tested against them. A validated code does not necessarily represent truth. It does represent a set of algorithms that have been shown, through a repeatable procedure, to perform according to according to
1. As stated or indicated by; on the authority of: according to historians.
2. In keeping with: according to instructions.
3. the current state of the art.
The NREL methodology for validating building energy simulation programs has been generally accepted by the International Energy Agency (Irving 1988), ASHRAE (ASHRAE 2001a, 2001b, 2004, 2006), and elsewhere with refinements suggested by other researchers (Bland 1992; Bloomfield 1988, 1999; Guyon and Palomo 1999; Irving 1988; Lomas 1991; Lomas and Bowman 1987; Lomas and Eppel 1992). Additionally, the Commission of European Communities European Community: see European Union.
European Community (EC)
Organization formed in 1967 with the merger of the European Economic Community, European Coal and Steel Community, and European Atomic Energy Community. has conducted considerable work under the PASSYS program (Jensen 1989; Jensen and van de Perre 1991).
EXAMPLES OF APPLYING THE NREL VALIDATION/TESTING METHODOLOGY
Herein is an example applying a portion of the above methodology to show how comparative tests can be used to extrapolate extrapolate - extrapolation beyond analytical verification test cases. The process is illustrated for testing the ability of simulation programs to model a simple split-system air conditioner conditioner,
n 1. an additive substance used to increase the effectiveness of another substance.
2. a substance added to enamel that improves a sealant's ability to adhere. using the steady-state analytical verification tests of HVAC BESTEST, Volume 1 (Neymark and Judkoff 2002), as the basis for further, more realistic, comparative tests of HVAC BESTEST, Volume 2 (Neymark and Judkoff 2004). Initially, Volume 1's analytical verification test cases were developed and distributed to IEA field-trial participants before analytical solutions were developed. The initial results are illustrated in Figure 2; these are "blind" results, meaning that the field-trial participants had no prior knowledge of each others' results. Development of steady-state analytical solutions after this initial round of simulations yielded a mathematical truth standard for the field-trial participants to compare to their results. Using this mathematical truth standard, the field-trial participants discovered and corrected a number of errors in their simulation programs. Such improvements to simulation programs or simulation inputs made by participants must have a mathematical and physical basis and must be applied consistently across tests. Also, all improvements were required to be documented in modeler reports. Arbitrary modification of a simulation program's input or internal code just for the purpose of more closely matching a given set of results is not allowed. The participants' corrections resulted in improved agreement among the simulation programs, as shown in Figure 3.
[FIGURE 1 OMITTED]
[FIGURE 2 OMITTED]
[FIGURE 3 OMITTED]
The HVAC BESTEST, Volume 2, comparative test cases, also applying a split-system air conditioner, were then developed. These cases include more realism (e.g., hourly varying internal gains and weather data, outside air mixing, etc.) such that obtaining analytical solutions outside the environment of a whole-building energy simulation program was not possible. Because these cases are an extension of the HVAC BESTEST, Volume 1, analytical verification test cases, it was possible to use results from the programs that were run and improved in the Volume 1 test cases and then further tested with Volume 2 as approximate benchmark results for comparing with programs that did not previously run the Volume 1 test cases. Figure 4 illustrates "blind" initial results for the Volume 2 comparative tests, while Figure 5 illustrates final Volume 2 comparative test results after technically justifiable corrections to the simulation programs were applied according to the rules previously stated. These figures show that because good agreement among simulations was achieved in the Volume 1 tests and because the Volume 2 tests are an extension of the the Volume 1 tests, there was some propagation of the level of agreement among simulations of the Volume 1 analytical verification tests through to the Volume 2 comparative test simulation results. There was also some further mprovement to the simulations achieved because of the Volume 2 comparative tests.
SUMMARY OF PREVIOUS AND CURRENT TESTING AND VALIDATION WORK
A summary of work in the areas of analytical verification, empirical validation, and comparative testing is available that cites and briefly summarizes approximately 100 articles and research reports covering work published from 1980 through mid-2001 (ASHRAE 2005; Neymark and Judkoff 2002). The following test suites have been completed and are in various stages of adaptation for Standard 140:
* Building energy simulation test and diagnostic method for heating, ventilating ventilating
Natural or mechanically induced movement of fresh air into or through an enclosed space. The hazards of poor ventilation were not clearly understood until the early 20th century. Expired air may be laden with odors, heat, gases, or dust. , and air-conditioning equipment models (HVAC BESTEST): Fuel-fired furnace test suite (Purdy and Beausoleil-Morrison 2003)
* Home energy rating system building energy simulation test (Judkoff and Neymark 1995b)
* International Energy Agency building energy simulation test and diagnostic method for heating, ventilating, and air-conditioning equipment models (HVAC BESTEST), Volume 2: Cases E300-E545 (Neymark and Judkoff 2004)
There are also a number of simulation test suites in various stages of completion that could eventually be included in Standard 140. These include, among others:
* ASHRAE RP-1052, Development of an analytical verification test suite for whole building energy simulation programs--Building fabric (Spitler et al. 2001)
* ASHRAE RP-865, Development of accuracy tests for mechanical system simulation (Yuill and Haberl 2002)
* RADTEST radiant heating radiant heating: see heating.
Heating system in which heat is transmitted by radiation from a heated surface. Radiant heating systems usually employ either electric-resistance wiring or hot-water heating pipes, which may embedded in and cooling test cases (Achermann and Zweifel 2003)
* Proposed IEA BESTEST ground-coupled cases (Deru et al. 2002)
* ETNA Etna or Aetna (both: ĕt`nə), volcano, 10,958 ft (3,340 m) high, on the east coast of Sicily, S Italy. It is the highest active volcano in Europe. BESTEST empirical validation test specification (Neymark et al. 2004)
* Daylighting--HVAC interaction tests for the empirical validation of building energy analysis tools (Maxwell et al. 2003)
* Economizer e·con·o·mize
v. e·con·o·mized, e·con·o·miz·ing, e·con·o·miz·es
1. To practice economy, as by avoiding waste or reducing expenditures.
2. control tests for the empirical validation of building energy analysis tools (Maxwell et al. 2004)
* A number of test suites that are being developed by National Renewable Energy Laboratory and researchers in International Energy Agency member nations under the auspices of IEA Solar Heating and Cooling Task 34 and IEA Energy Conservation in Buildings and Community Systems Annex 43 (IEA SHC SHC Sears Holdings Corporation (Hoffman Estates, ILt)
SHC Self-Help Clearinghouse (Valley Cottage, NY)
SHC Spring Hill College (Mobile, AL, USA)
SHC Solar Heating and Cooling 34/ECBCS 43) (Judkoff and Neymark 2004).
CONCLUSION AND RECOMMENDATIONS
New material has been added to the 2005 ASHRAE Handbook--Fundamentals (ASHRAE 2005) that describes a method to evaluate the accuracy of whole-building energy simulation programs and to identify and diagnose differences in simulation predictions that may be caused by algorithmic differences, modeling limitations, coding errors, or input errors. This methodology, which was developed by the NREL beginning over 20 years ago (Judkoff et al. 1983b), has been adopted by ANSI/ASHRAE Standard 140, Method of Test for the Evaluation of Building Energy Analysis Computer Programs (ASHRAE 2001a, 2004). The current set of test cases included in Standard 140 occupy only a small area of the parameter space represented by the cells in the methodological test matrix described in this paper. Additional suites of test cases have been developed that can be considered for integration into Standard 140. We recommend more work to integrate such existing test suites into Standard 140.
Some high-priority areas for additional test cases are:
* Comparative tests -- Mechanical equipment (additional tests beyond those in HVAC BESTEST unitary cooling and heating equipment cases)
* Analytical verification -- Mechanical equipment (additional tests beyond those in RP-865 and HVAC BESTEST unitary cooling and heating equipment test cases)
* Empirical validation -- Mechanical equipment (additional tests beyond those in IEA SHC Task 22 and IEA SHC Task 34/ECBCS Annex 43)
More work to develop such test suites is recommended.
Standard 140 and/or the reports that comprise the test suites contained therein (commonly known as the NREL BESTEST reports) are being referenced and used by a growing number of code promulagation authorities throughout the world. ASHRAE Standard 90.1 (ASHRAE 2001b, 2006) requires that software used for demonstrating performance compliance with Standard 90.1 be tested using ASHRAE Standard 140. Standard 90.1 is ASHRAE's consensus energy code for commercial buildings and for non-low-rise residential buildings. IEA BESTEST is also being used for simulation certification tests in The Netherlands (ISSO See CSO. 2003), Australia (SEDA SEDA Staff and Educational Development Association
SEDA Sustainable Energy Development Authority (Australia)
SEDA Social and Economic Data Analysis
SEDA Special Ed Assistant
SEDA South East Drift Association 2003; Pears 1998), New Zealand New Zealand (zē`lənd), island country (2005 est. pop. 4,035,000), 104,454 sq mi (270,534 sq km), in the S Pacific Ocean, over 1,000 mi (1,600 km) SE of Australia. The capital is Wellington; the largest city and leading port is Auckland. (Donn 2004), and Portugal (Maldonado 2005). As part of their building energy performance assessments under the European Community's Energy Performance Directive (European Union European Union (EU), name given since the ratification (Nov., 1993) of the Treaty of European Union, or Maastricht Treaty, to the
European Community 2002), Austria, Denmark, Greece, and The Netherlands are using a new software tool that includes algorithms that have been checked with BESTEST (Balaras et al. 2005). Also, CEN CEN - Conseil Européen pour la Normalisation.
A body coordinating standardisation activities in the EEC and EFTA countries. has utilized BESTEST to check their reference cooling load calculation general criteria of prEN ISO (1) See ISO speed.
(2) (International Organization for Standardization, Geneva, Switzerland, www.iso.ch) An organization that sets international standards, founded in 1946. The U.S. member body is ANSI. 13791 (CEN 2004a) and simplified methods of prEN ISO 13792 (CEN2004b; Millet millet, common name for several species of grasses cultivated mainly for cereals in the Eastern Hemisphere and for forage and hay in North America. The principal varieties are the foxtail, pearl, and barnyard millets and the proso millet, called also broomcorn millet 2003). In the United States, the National Association of State Energy Officials (NASEO NASEO National Association of State Energy Officials ) Residential Energy Services Network (RESNET) has adopted Home Energy Rating System (HERS) BESTEST (Judkoff and Neymark 1995b) as the basis for certifying software to be used for home energy rating systems under the NASEO/RESNET national accreditation standard (NASEO/RESNET 2002). This is indicative of the importance of validation methods for improving the state of the art in building energy software and for helping to certify such software for use with home energy rating standards, building energy codes, building energy tax credits, and other building energy incentive programs. The importance of validation and test methods is further supported by a recent report comparing 20 whole-building energy simulation tools (Crawley et al. 2005). The report indicates that 18 of the 20 tools reviewed have been tested with at least one of the two procedures currently included in ASHRAE Standard 140-2004, 7 of the tools have been tested with both procedures, and 9 of the tools have been tested with three additional procedures that are currently in various stages of adaptation for Standard 140.
[FIGURE 4 OMITTED]
[FIGURE 5 OMITTED]
Extensively reducing the energy intensity of buildings through better design is possible with the use of simulation tools. However, widespread use of building energy simulation software Simulation software is based on the process of imitating a real phenomenon with a set of mathematical formulas. It is, essentially, a program that allows the user to observe an operation through simulation without actually running the program. will not occur unless the design and engineering communities have confidence in these programs. The work described here represents a good start in the effort to develop rigorously validated building energy simulation tools.
We appreciate the support and guidance of D. Crawley, DOE Program Manager for Simulation Tools and representative to the IEA Solar Heating and Cooling Programme Executive Committee. Also appreciated is the support and guidance of R. Karney, DOE Program Manager and representative to the IEA Energy Conservation in Buildings and Community Systems Executive Committee.
Adaptation of the pre-normative IEA research into an ASHRAE Standard Method of Test was assisted by the help and guidance of the members of the SSPC 140 standing committee and the preceding SPC 140 committee: C. Barnaby, I. Beausoleil-Morrison, D. Crawley, P. Fairey, K. Fraser, J. Haberl, D. Knebel, B. Maeda, S. Rees, R. Sonderegger, J. Spitler, G. Walton, B. Wilcox, F. Winkelmann, M. Witte, and G. Yuill. We also gratefully acknowledge the significant contributions to this work from the members of IEA SHC Tasks 8, 12, and 22, and IEA ECBCS ECBCS Energy Conservation in Buildings and Community Systems (Programme) Annex 21.
Achermann, M., and G. Zweifel. 2003. RADTEST--Radiant Heating and Cooling Test Cases. Horw-Lucerne, Switzerland: University of Applied Sciences Central Switzerland Central Switzerland is the region of the Alpine foothills geographically the heart and historically the origin of Switzerland, with the cantons of Uri, Schwyz, Obwalden, Nidwalden, Lucerne and Zug.
Central Switzerland is one of the NUTS 2 Statistical Regions. , Lucerne Lucerne (lsûrn`), Ger. Luzern (ltsĕrn`), canton (1993 pop. School of Architecture. http://www.iea-shc.org/task22/reports/RADTEST_final.pdf.
ASHRAE. 2001a. ANSI/ASHRAE Standard 140-2001, Standard Method of Test for the Evaluation of Building Energy Analysis Computer Programs. Atlanta: American Society of Heating, Refrigerating re·frig·er·ate
tr.v. re·frig·er·at·ed, re·frig·er·at·ing, re·frig·er·ates
1. To cool or chill (a substance).
2. To preserve (food) by chilling. and Air-Conditioning Engineers, Inc.
ASHRAE. 2001b. ANSI/ASHRAE/IESNA Standard 90.1-2001, Energy Standard for Buildings Except Low-Rise Residential Buildings, Addendum addendum n. an addition to a completed written document. Most commonly this is a proposed change or explanation (such as a list of goods to be included) in a contract, or some point that has been subject of negotiation after the contract was originally proposed by p. Atlanta: American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc.
ASHRAE. 2004. ANSI/ASHRAE Standard 140-2004, Standard Method of Test for the Evaluation of Building Energy Analysis Computer Programs. Atlanta: American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc.
ASHRAE. 2005. 2005 ASHRAE Handbook--Fundamentals. Chapter 32, Energy Estimating and Modeling Methods, section "Model Validation and Testing." Atlanta: American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc.
ASHRAE. 2006. ANSI/ASHRAE/IESNA Standard 90.1-2004, Energy Standard for Buildings Except Low-Rise Residential Buildings, Addendum l. Atlanta: American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (1)
Balaras, C.A., B. Poel, and G. van Crutchen. 2005. Software for energy performance assessment of existing dwellings. IBPSA IBPSA International Building Performance Simulation Association News 15(1):24-31. International Building Performance Simulation Association, April.
Bland, B. 1992. Conduction in dynamic thermal models: Analytical tests for validation. BSER BSER Brain Stem Evoked Response (Audiology) & T 13(4):197-208.
Bloomfield, D. 1988. An Investigation into Analytical and Empirical Validation Techniques for Dynamic Thermal Models of Buildings. Vol. 1, Executive Summary. SERC/BRE final report. Garston, Watford, UK: BRE (Business Rules Engine) Software that automates policies and procedures within an organization, whether legal, internal or operational. The use of a rules engine (BRE) requires placing the company rules in an external repository that can be easily reviewed rather than .
Bloomfield, D. 1999. An overview of validation methods for energy and environmental software. ASHRAE Transactions 105(2):685-93.
CEN. 2004a. prEN ISO 13791, Thermal performance of buildings--Calculation of internal temperatures of a room in summer without mechanical cooling--General criteria and validation procedures. Final draft. Comite Europeen de la Normalisation 1. (data processing) normalisation - A transformation applied uniformly to each element in a set of data so that the set has some specific statistical property. For example, monthly measurements of the rainfall in London might be normalised by dividing each one by the total , Brussels.
CEN. 2004b. prEN ISO 13792, Thermal performance of buildings--Calculation of internal temperatures of a room in summer without mechanical cooling--Simplified methods. Final draft. Comite Europeen de la Normalisation, Brussels.
Crawley, D., J. Hand, M. Kummert, and B. Griffith. 2005. Contrasting the Capabilities of Building Energy Performance Simulation Programs. Washington, DC: US Department of Energy; Glasgow, Scotland, UK: University of Strathclyde The University of Strathclyde (Scottish Gaelic: Oilthigh Srath Chluaidh) is a university in Glasgow, Scotland. History
The university originated as Anderson's Institution in 1796. ; Madison, WI: University of Wisconsin. http://gundog.lbl.gov/dirpubs/2005/05_compare.pdf.
Deru, M., R. Judkoff, and J. Neymark. 2002. Proposed IEA BESTEST Ground-coupled Cases, draft. National Renewable Energy Laboratory, Golden, CO. July.
Donn, M. 2004. May 2004 e-mail communication with R. Judkoff and J. Neymark. Victoria University, Victoria, New Zealand.
European Union. 2002. On the energy performance of buildings. Directive 2002/91/EC of the European Parliament European Parliament, a branch of the governing body of the European Union (EU). It convenes on a monthly basis in Strasbourg, France; most meetings of the separate parliamentary committees are held in Brussels, Belgium, and its Secretariat is located in Luxembourg. and of the Council. Official Journal of the European Communities, December.
Guyon, G., and E. Palomo. 1999. Validation of two French building energy analysis programs, Part 1: Analytical verification. ASHRAE Transactions 105(2):694-708.
Hunn, B.D., W.V. Turk, and W.O. Wray. 1982. Validation of Passive Solar
Passive solar technologies convert sunlight into usable heat, cause air-movement for ventilation or cooling, or store heat for future use, without Analysis/Design Tools Using Class A Performance Evaluation Performance evaluation
The assessment of a manager's results, which involves, first, determining whether the money manager added value by outperforming the established benchmark (performance measurement) and, second, determining how the money manager achieved the calculated return Data. LA-UR-82-1732. Los Alamos Los Alamos (lôs ăl`əmōs', lŏs), uninc. town (1990 pop. 11,455), seat of Los Alamos co., N central N.Mex. It is on a long mesa extending from the Jemez Mts. The U.S. , NM: LANL LANL - Los Alamos National Laboratory, Los Alamos, NM, USA. .
Irving, A. 1988. Validation of dynamic thermal models. Energy and Buildings, January. Lausanne, Switzerland: Elsevier Sequoia, S.A.
ISSO. 2003. Energie Diagnose Referentie Versie 3.0 (in Dutch). ISSO Publicatie 54. Rotterdam, The Netherlands: Institut voor Studie en Stimulering van Onderzoekop Het Gebied van Gebouwinstallaties.
Jensen, S., ed. 1989. The PASSYS Project Phase 1--Subgroup model validation and development, Final report--1986-1989. Commission of the European Communities, Directorate General XII.
Jensen, S., and R. van de Perre. 1991. Tools for whole model validation of building simulation programs, Experience from the CEC (Central Electronic Complex) The set of hardware that defines a mainframe, which includes the CPU(s), memory, channels, controllers and power supplies included in the box. Some CECs, such as IBM's Multiprise 2000 and 3000, include data storage devices as well. Concerted Action PASSYS. Proceedings of Building Simulation '91, August 20-22, Nice, France.
Judkoff, R. 1988. Validation of building energy analysis simulation programs at the Solar Energy solar energy, any form of energy radiated by the sun, including light, radio waves, and X rays, although the term usually refers to the visible light of the sun. Research Institute. Energy and Buildings 10(3):235. Lausanne, Switzerland: Elsevier Sequoia.
Judkoff, R., and J. Neymark. 1995a. International Energy Agency building energy simulation test (BESTEST) and diagnostic method, NREL/TP-472-6231. National Renewable Energy Laboratory, Golden, CO. http://www.nrel.gov/docs/legosti/old/6231.pdf.
Judkoff, R., and J. Neymark. 1995b. Home energy rating system building energy simulation test (HERS BESTEST), NREL/TP-472-7332. National Renewable Energy Laboratory, Golden, CO. http://www.nrel.gov/docs/legosti/fy96/7332a.pdf. http://www.nrel.gov/docs/legosti/fy96/ 7332b.pdf.
Judkoff, R. (operating agent), and J. Neymark. 2004. IEA SHC Task 34/ECBCS Annex 43, Testing and validation of building energy simulation tools. Annex document. International Energy Agency: Solar Heating and Cooling Programme, and Energy Conservation in Buildings and Community Systems, Paris, France.
Judkoff, R., D. Wortman, and J. Burch. 1983a. Measured versus predicted performance of the SERI SERI Sustainable Europe Research Institute
SERI Special Education Resources on the Internet
SERI Solar Energy Research Institute (Golden, Colorado)
SERI Singapore Eye Research Institute
SERI Schepens Eye Research Institute test house: A validation study, SERI/TP-254-1953. Solar Energy Research Institute (now National Renewable Energy Laboratory), Golden, CO.
Judkoff, R., D. Wortman, C. Christensen, B. O'Doherty, D. Simms, and M. Hannifan. 1980. A comparative study of four passive building energy simulations: DOE-2.1, BLAST, SUNCAT-2.4, DEROB-III. SERI/TP-721-837. UC-59c. Solar Energy Research Institute (now National Renewable Energy Laboratory), Golden, CO.
Judkoff, R., D. Wortman, B. O'Doherty, and J. Burch. 1983b. A methodology for validating building energy analysis simulations, SERI/TR-254-1508. Solar Energy Research Institute (now National Renewable Energy Laboratory), Golden, CO.
Lomas, K. 1991. Dynamic thermal simulation models of buildings: New method of empirical validation. BSER & T 12(1):25-37.
Lomas, K., and N. Bowman. 1987. Developing and testing tools for empirical validation. Chapter 14, Vol. IV of SERC/BRE final report, An investigation in analytical and empirical validation techniques for dynamic thermal models of buildings. BRE, Garston, Watford, UK.
Lomas, K., and H. Eppel. 1992. Sensitivity analysis techniques for building thermal simulation programs. Energy and Building (19)1:21-44.
Lomas, K., H. Eppel, C. Martin, and D. Bloomfield. 1994. Empirical validation of thermal building simulation programs using test room data. Vol.1, Final report. International Energy Agency Report #IEA21RN399/94. Vol. 2, Empirical Validation Package (1993), IEA21RR5/93. Vol. 3, Working Reports (1993), IEA21RN375/93. De Montfort University De Montfort University (DMU) is a British university situated in Leicester, England. History
De Montfort University, which is named after Simon de Montfort who was Earl of Leicester in the 13th century, is one of two universities situated in the , Leicester, UK.
Maldonado, E. 2005. Energy certification of buildings in Portugal. Presentation at Joint IEA ECBCS/SHC Executive Committee Meeting, Technical Day, June 15, 2005, Espinho, Portugal.
Maxwell, G., P. Loutzenhiser, and C. Klaassen. 2003. Day-lighting--HVAC interaction tests for the empirical validation of building energy analysis tools. Iowa State University Academics
ISU is best known for its degree programs in science, engineering, and agriculture. ISU is also home of the world's first electronic digital computing device, the Atanasoff–Berry Computer. , Department of Mechanical Engineering, Ames, IA.
Maxwell, G., P. Loutzenhiser, and C. Klaassen. 2004. Economizer control tests for the empirical validation of building energy analysis tools, Draft. Iowa State University, Department of Mechanical Engineering, Ames, IA.
Millet, J.-R. 2003. Personal communication at IEA SHC Task Definition Workshop, April 24-25, 2003, Delft Delft (dĕlft), city (1994 pop. 91,941), South Holland prov., W Netherlands. It has varied industries and is noted for its ceramics (china, tiles, and pottery) known as delftware. Founded in the 11th cent. , Netherlands. Centre Scientifique et Technique du Batiment, Paris, France.
Morck, O. 1986. Simulation model validation using test cell data. IEA SHC Task VIII, Report #176, Thermal Insulation The term thermal insulation can refer to materials used to reduce the rate of heat transfer, or the methods and processes used to reduce heat transfer.
Heat is transferred from one material to another by conduction, convection and/or radiation. Laboratory, Technical University of Denmark The Technical University of Denmark (Danish: Danmarks Tekniske Universitet, DTU) was founded in 1829 as the 'College of Advanced Technology' (Danish: Den Polytekniske Læreanstalt). , Lyngby, Denmark.
NASEO/RESNET. 2002. Mortage industry national home energy rating systems accreditation standards. Residential Energy Services Network, Oceanside, CA. June 15, 2002. www.natresnet.com.
Neymark, J., P. Girault, G. Guyon, R. Judkoff, R. LeBerre, J. Ojalvo, and P. Reimer. 2004. ETNA BESTEST empirical validation test specification. J. Neymark & Associates, Golden, Colo.; Electricite de France, Moret sur Loing, France. In collaboration with National Renewable Energy Laboratory, Golden, CO.
Neymark, J., and R. Judkoff. 2002. International Energy Agency Building Energy Simulation Test and Diagnostic Method for Heating, Ventilating, and Air-Conditioning Equipment Models (HVAC BESTEST), Volume 1: Cases E100-E200. NREL/TP-550-30152. Golden, CO: National Renewable Energy Laboratory. http://www.nrel.gov/docs/fy02osti/30152.pdf.
Neymark, J., and R. Judkoff. 2004. International Energy Agency Building Energy Simulation Test and Diagnostic Method for Heating, Ventilating, and Air-Conditioning Equipment Models (HVAC BESTEST), Volume 2: Cases E300-E545. NREL/TP-550-36754. Golden, CO: National Renewable Energy Laboratory. http://www.nrel.gov/docs/fy05osti/36754.pdf.
Pears, A. 1998. Rating energy efficiency of non-residential buildings: A path forward for New South Wales New South Wales, state (1991 pop. 5,164,549), 309,443 sq mi (801,457 sq km), SE Australia. It is bounded on the E by the Pacific Ocean. Sydney is the capital. The other principal urban centers are Newcastle, Wagga Wagga, Lismore, Wollongong, and Broken Hill. . Report for the Sustainable Energy
Sustainable energy sources are energy sources which are not expected to be depleted in a timeframe relevant to the human race, and which Development Authority. Sustainable Solutions Pty Ltd PTY LTD Propriety Limited (company structure in Australia) ., Brighton, Victoria Brighton is a suburb in Melbourne, Victoria, Australia, 12 km southeast of the city. Much of the suburb lies on the shore of Port Phillip Bay. Notable Residents
Purdy, J., and I. Beausoleil-Morrison. 2003. Building energy simulation test and diagnostic method for heating, ventilating, and air-conditioning equipment models (HVAC BESTEST): Fuel-fired furnace test cases. Natural Resources Canada Natural Resources Canada (NRCan) is a department of the government of Canada responsible for natural resources, energy, minerals and metals, forests, earth sciences, mapping and remote sensing. , CANMET CANMET Canada Centre for Mineral and Energy Technology Energy Technology Centre, Ottawa, Canada. http://www.iea-shc.org/task22/deliverables.htm.
SEDA. 2003. Guidelines for the use of simulation in commitment agreements. Sustainable Energy Development Authority, Grosvenor Place Grosvenor Place may refer to:
Spitler, S., S. Rees, and D. Xiao. 2001. Development of an analytical verification test suite for whole building energy simulation programs--Building fabric. Final report for ASHRAE 1052-RP. Oklahoma State University Oklahoma State University, at Stillwater; land-grant and state supported; coeducational; chartered 1890, opened 1891 as Oklahoma Agricultural and Mechanical College, renamed 1957. School of Mechanical and Aerospace Engineering, Stillwater, OK.
Yuill, G., and J. Haberl. 2002. Development of accuracy tests for mechanical system simulation. Final Report for ASHRAE 865-RP. University of Nebraska, Omaha, NE.
Joel Neymark, PE
Ron Judkoff is director of the Buildings & Thermal Systems Center at the National Renewable Energy Laboratory, Golden, Colo., and is chair of ASHRAE Standing Standard Project Committee (SSPC) 140. Joel Neymark is director of J. Neymark & Associates, Lakewood, Colo., and is vice-chair of SSPC 140.
(1). References ANSI/ASHRAE Standard 140-2004. Addendum l has passed through the ASHRAE review process and is expected to be published during mid-2006.
Table 1. Validation Techniques Technique Advantages Disadvantages Empirical * Approximate truth * Experimental Test of model and solution standard within uncertainties: process experimental accuracy -Instrument * Any level of calibration, spatial/ complexity temporal discretization -Imperfect knowledge/ specification of experimental object (building) being simulated * High-quality detailed measurements are expensive and time consuming * Only a limited number of test conditions are practical Analytical * No input * No test of model Test of solution process uncertainty validity * Exact mathematical * Limited to highly truth standard for constrained cases the given model for which analytical * Inexpensive solutions can be derived Comparative * No input * No absolute truth Relative test of model and uncertainty standard (only solution process * Any level of statistically-based complexity acceptance ranges * Many diagnostic are possible) comparisons possible * Inexpensive and quick Table 2. Types of Extrapolation Obtainable Data Points Extrapolation A few climates Many climates Short-term total energy usage Long-term total energy usage or vice versa Short-term (hourly) temperatures Long-term total energy usage or and/or fluxes vice versa A few equipment performance points Many equipment performance points A few buildings representing a few Many buildings representing many sets of variable and parameter sets of variable and parameter combinations combinations or vice versa Small-scale: simple test cells, Large-scale complex buildings with buildings, and mechanical systems; complex HVAC systems or vice laboratory experiments versa